2010 Loren Cook 600 CF Centrifugal Blower, Backwards Inclined, Up Blast, Class II System with Baldor 100Hp Motor. According to the chart this system will produce 106,000 CFM @ 1.5" Static Pressure. This system has had very little use and is in excellent condition. We also have a Control Techniques SP5401 Variable Frequency Drive we can sell with this system for an additional $6500.00. This is a large blower and will require wide load permits to ship. The narrow side of the system measures over 9' even with the belt gaurd removed.
- Model: 600 CF
- Series: CF Series
- Serial Number: 062SD21527 01/0000701
- MFG Date: June 2010
- Type: Centrifugal Blower
- Construction: Class II
- Horsepower: 100Hp
- RPM: 822 RPM
- CFM: 106,000 CFM @ 1.5" Static Pressure
- Orientation: Up Blast
- Rotation: CW
- Intake Opening Diameter: 60" O.D.
- Discharge Opening: 69 1/2" Long x 50" Wide (Measurements are from outside flange to outside flange)
- Motor Brand: Baldor
- Motor Model: M4400T
- Motor Voltage: 230-460Vac 3 Phase
- Motor Amperage: 232 / 116 Amps
- Motor RPM: 1780
- Motor Frame: 405T
Description: Fan shall be a single width, single inlet backward inclined flat blade, belt driven centrifugal blower. Certifications: Fan shall be manufactured at an ISO 9001 certified facility. Fan shall be listed by Underwriters Laboratories (UL/cUL 705) for US and Canada. For restaurant applications, fan shall be listed by Underwriters Laboratories (UL/cUL 762) for US and Canada. For smoke control applications, fan shall be listed by Underwriters Laboratories (Power Ventilator for Smoke Control Systems) for US and Canada. Fan shall bear the AMCA Certified Ratings Seal for Sound and Air Performance. Construction: The fan shall be of bolted and welded construction utilizing corrosion resistant fasteners. The scroll wrapper and scroll side panels shall be a minimum 12 gauge steel. The entire fan housing shall have continuously welded seams for leakproof operation and shall have a minimum 1 ½” outlet discharge flange. A performance cut-off shall be furnished to prevent the recirculation of air in the fan housing. Bearing support shall be minimum 10 gauge welded steel. Lifting eyes shall be provided for ease of installation. Unit shall bear an engraved aluminum nameplate. Nameplate shall indicate design CFM, static pressure, and maximum fan RPM. Unit shall be shipped in ISTA certified transit tested packaging. Coating: Steel fan components shall be LORENIZED™ with an electrostatically applied, baked polyester powder coating. Each component shall be subject to a five stage environmentally friendly wash system, followed by a minimum 2 mil thick baked powder finish. Paint must exceed 1,000 hour salt spray under ASTM B117 test method. Wheel: Wheel shall be steel, non-overloading, centrifugal backward inclined, flat blade type. Blades shall be continuously welded to the backplate and deep spun inlet shroud. All sizes shall be keyed and securely attached to the fan shaft. Wheel shall overlap an aerodynamic aluminum inlet cone to provide maximum performance and efficiency. Wheel shall be balanced in accordance with AMCA Standard 204-05, Balance Quality and Vibration Levels for Fans. Motor: Motor shall be NEMA Design B with Class B insulation rated for continuous duty and furnished at the specified voltage, phase and enclosure. Bearings: Bearings shall be designed and tested specifically for use in air handling applications. Construction shall be heavy duty regreasable ball or roller type in a cast iron pillow block housing selected for a minimum L50 life in excess of 200,000 hours at maximum cataloged operating speed. Blower Shaft: Blower shaft shall be AISI C-1045 hot rolled and accurately turned, ground and polished. Shafting shall be sized for a critical speed of at least 125% of maximum RPM. Belts and Drives: Belts shall be oil and heat resistant, static conducting. Drives shall be precision machined cast iron type, keyed and securely attached to the wheel and motor shafts. Drives shall be sized for 150% of the installed motor horsepower. The variable pitch motor drive must be factory set to the specified fan RPM. Product: Fan shall be model CF as manufactured by Loren Cook Company of Springfield, Missouri.